Si tienes problemas para ingresar: puedes escribir a [email protected] para soporte técnico.
Iniciado por Yorkhesan, junio 26, 2013, 03:52:43 pm
CitarRazones por las que la luz LED se iluminará el cableado del sitio:1. Sobrecarga cable neutro.2. La polaridad invertida (cables de corriente y neutro están invertidos). 3. Falta el cable de tierra.
Cita de: "felipelvrd"En una búsqueda rápida encontré:Apareció de repente o todo el tiempo ha estado así?
CitarSite Wiring Fault or Building Wiring Fault Indicator LED is onSolution The Site Wiring Fault LED light is only present on 120V UPS and Surge products. On APC UPS products this indicator is typically on the rear panel. The purpose of this indicator light is to warn you that there are problems with your building wiring that may result in a shock hazard.APC recommends that you have a qualified electrician inspect your wiring for one or more of the conditions listed below.Reasons why the Site Wiring LED light will illuminate:1. Overloaded neutral wire.2. Reversed polarity (hot and neutral wires are reversed).3. Missing ground wire.If the outlet that the APC UPS unit is plugged into is not properly grounded or properly wired, the surge protection capability of our unit may be diminished. Therefore, in order to maintain your warranty and protection under APC's Equipment Protection Policy, be sure that the APC unit is only plugged into a properly grounded outlet where the Site Wiring Fault Indicator (SWFI) light is not illuminated.All of APC's UPSs with the exception of the Matrix-UPS and the Symmetra Power Array have a small red LED light that is called a SWFI. On some UPS models, this LED is referred to as the Building Wiring Fault Indicator. Both have the same function. On most UPS models, the light is located on the rear of the unit near where the output receptacles are located.
Page generada en 0.212 segundos con 19 consultas.